Starting price from £295.00 for a three bedroom house approximately 7 radiators. It is always advisable to change old radiator valves before power flushing commences as they may probably leak once turned and this is an ideal time to upgrade or renew TRV's (Thermostatic Radiator Valves).
POWER FLUSH! All of our engineers have attended training courses with Kamco, a leading manufacturer of power flushing pumps and chemicals.
All existing heating systems with new boiler installations are certificated and guaranteed to be sludge free and efficient. This protects the boiler from damage and also maintains a trouble free Manufacturers warranty.
The objective is to restore systems with circulation and boiler noise problems (caused by sludge and corrosion deposits) to optimum operation. Power flushing removes these deposits and the problems that they cause.
It is prudent to power flush a heating system immediately before fitting a new boiler to an existing system to prevent possible future problems. Many systems are found to contain corrosion and sludge, even if no flow problems have yet shown themselves.
Existing debris is often mobilised by alterations to the system/piping and the increased efficiency of the new boiler, and may then accumulate in the boiler heat exchanger, causing noisy operation, reduced efficiency and, in extreme circumstances, failure of the boiler.
The high efficiency and compactness of modern boilers, developed to minimise fuel costs and pollution, means that they are more susceptible to problems caused by debris in the system water.
The KAMCO CLEARFLOW Power Flushing pump is simply connected into the heating system, either across standard circulator pump couplings, across the tails of one radiator, or wherever most practicable.
The powerful flow, combined with instantaneous flow reverser device, will dislodge and mobilise deposits and corrosion which resist traditional system cleaning methods.
Once the corrosion and sludge deposits have been loosened and mobilised, fresh clean water is forced through the heating system, pushing the contaminated water out through a full bore dump valve to waste.
During the Power flushing process, radiators are individually flushed, without removing or disconnecting them from the system, by directing the full output of the pump through each radiator separately.
At the end of the Power Flushing process, the system contains fresh clean water and reinstatement of the system to normal operation takes only a few minutes.
System Power Flushing will not remedy design or mechanical faults, which should be rectified, but in many cases it will cure the problems caused by these.